The advantage of the spiral duct machine is that the installation significantly reduces the connection point between the tube and the tube, minimizing the leakage of the tube joint. The typical length of the spiral duct is 3 to 6 m, and the length of a typical rectangular duct is typical. Only 1~1.5m; and only one pipe joint is required to connect two spiral ducts, and the traditional rectangular duct connection often requires a completely independent double flange system. Let MYT introduce you the design of the duct system.
This requires the most important guidelines for the layout of any duct system. The linearly arranged duct system is the lowest in both operational energy consumption and initial investment. From the point of view of energy saving, air always "hopes" to go straight, which will reduce energy consumption. From the perspective of cost, the cost of straight pipe sections is much less than that of various elbows. Therefore, when arranging the plane of a duct system, the stress map minimizes the number of turns.
Straight, standard length ducts are relatively inexpensive to manufacture because of their low processing costs and standard length straight ducts that can be produced on a white line in accordance with standard width steel coils. Any of the non-standard length rectangular ducts can be technically used as accessories because they cannot be made of standard coils. The spiral circular duct can be made to any length. The standard length of the elliptical duct is completely dependent on the processing standard of the metal processing plant. Some designers always think that in flat design of a duct system, it is possible to reduce the size of the duct section frequently, which seems to reduce one investment. But it's actually not. Using four reducer tubes to reduce the length of each straight pipe section is not as good as increasing the length of the standard straight pipe section, but reducing the variable pipe to one, the latter Investment and operating energy costs can be reduced.
The circular duct allows for higher wind speeds. According to the recommendation of the American Society of Heating, Refrigerating and Air-Conditioning Engineers, a medium-sized variable air volume air-conditioning system with a wind speed of up to 20 m/s, and a large variable air volume control system with a wind speed of up to 30 m/s. The allowable wind speed for the rectangular duct is generally low. If the wind speed is too high, the flat duct wall will resonate to generate noise, especially low-frequency noise will be transmitted to the room. With a round duct and a high air supply speed, significant investment savings can be achieved. First, a circular duct system can save 15% to 30% of sheet steel compared to a similar rectangular duct system. For example, the same air is delivered at 17000m3/h. According to the requirements of control noise, the wind speed of the circular duct can be 19m/s, and the rectangular duct is 10m/s.
Secondly, the installation cost of the circular duct is lower than that of the rectangular duct. This is because the circular duct itself has a good rigidity, the prefabricated pipe section can be long, and the workload on the field installation is relatively small. The circular duct is made and connected more rigidly than the rectangular duct. The air leakage rate is about 1%, and the air leakage rate of the rectangular duct is sometimes as high as 10% or even higher. To prevent air leakage, it takes a lot of manpower. Each rectangular duct is leak tested and sealed.
As a professional spiral duct forming machine manufacturer, MYT machinery always provide good quality and good after-sales, also ensure spiral pipe good sealing performance and perfect pipe appearance.